Since field labor is expensive, the collector housing should be designed such
that the collector units can be quickly secured in place and connected to the
external piping. Provisions should also be made for easy replacement of
broken glass covers. The absorber plate should be mounted so as to be
thermally isolated as much as possible from the housing.
2.1.6 Collector gaskets and sealants. Gaskets and sealants must be
carefully selected if a collector is to have a long life. Generally, the
housing and the glazing have different rates of thermal expansion. Gaskets
and sealants form the flexible interface between the two components and seal
out moisture and other contaminants; if they fail, moisture will fog the
glazing and may possibly damage the absorber coating and the insulation.
These problems can drastically reduce the thermal performance of the
Two suitable sealing methods are shown in Figures 2-2 and 2-3 (Montgomery,
1978). The gaskets provide flexible support and the primary weather sealant
insures against moisture leakage. Desiccants are sometimes placed between
the two glazings to absorb any moisture that may remain after cover
installation. When selecting collector gaskets and sealants, certain
Withstand significant expansion and contraction without destruction.
Adhere effectively to all surfaces.
Resist ultraviolet degradation.
Resist outdoor weathering.
Not harden or become brittle.
Withstand temperature cycling from -30 deg. to 400 deg. F.
Not outgas at high temperatures.