k) A waste tank or means to dispose of fuel samples.
l) Lighted exit signs.
m) Capabilities to maintain laboratory at 73
degrees F (23 degrees C) plus or minus 5 degrees F (3
degrees C). (Required to protect laboratory equipment.)
n) Bonding and grounding of all metal working
surfaces and electrical equipment. Also, provide a common
static grounding strap or approved grounding points readily
accessible to all fixed working surfaces and alongside
o) Recessed floor to prevent spilled fuel from
flowing into adjacent areas.
p) Windows constructed of fireproof materials.
Draperies and curtains are prohibited. If interior windows
are provided, use translucent reinforced safety glass.
q) An HVAC system designed so that air from the
laboratory does not recirculate to other portions of the
r) Floor drains.
s) Interior separations from other portions of the
building with a partition rated for fire separation as
required by NFPA 45.
t) Type "N" unprotected non-combustible
Miscellaneous Safety Equipment. Provide
firefighting, fire alarm, and emergency eyewash/shower
Control Room. Where computerized control equipment
is anticipated, provide a control room of adequate size and