(10) Remove automatic water drains on
filter/separators and ensure that any liquid drained from
separators is properly handled.
e) Add isolation valves and blind flanges throughout
f) Use smart pigging to determine the condition of
the distribution piping.
g) Monitor, remove, and dispose of petroleum-
h) Spill Containment and Collection.
(1) Concrete containment areas for dikes,
equipment pads, fill stands, etc.
(2) Impervious lining system for dikes,
containment areas, and catch basins.
(3) Oil/water separators for treatment of
stormwater discharges from containment areas (e.g., dike
areas, fill stands, equipment pads, etc.). Refer to Section 2
of this handbook for additional information.