18.104.22.168 Emergency Shower and Eye Wash Fountain. Provide an emergency shower and eye
wash fountain, meeting ANSI Z358.1, within any work area in which personnel eyes or body
may be accidentally exposed to injurious corrosive materials.
Piping and Equipment
Piping. Provide safety relief valves on piping in accordance with ANSI/ASME
B31.1, Power Piping (ASME Code for Pressure Piping).
receivers, heat exchangers, and other pressure vessels in accordance with the ASME
Boiler and Pressure Vessel Code.
discharge valve is closed with the equipment in operation.
Equipment Enclosures. To protect both equipment and personnel, provide
enclosures for batteries, machine shop, and laboratory equipment. Battery rooms shall
be provided with forced ventilation exhaust type fans.
Air Navigation. To determine if any part of the power plant, such as the
stack, presents an obstruction to air navigation, refer to Title 14 Code of Federal
Regulations, Part 77. See also Federal Aviation Administration advisory circular AC
70/7460-1F, Obstruction Marking and Lighting; FAA 150/5345-43c, Specification for
2, General Requirements for Shorebased Airfield Marking and Lighting.
See NAVFAC DM-5.12,Fencing, Gates, and Guard Towers,