(4) The commercial size rectifier meeting the above
requirements is 115-V, single-phase, selenium, and full-wave bridge type
having a dc output of 8 A, and 8 V.
i) Rectifier location. Mount the rectifier at eye level on a
separate pole adjacent to an existing overhead electrical distribution sy
9.5 Gas Distribution System. Galvanic cathodic protection is designed
for a gas distribution system in a housing area as shown in Figure 108.