1 January 2001
Table 2-17. Halon Systems ITM Tasks (Continued)
6. Auxiliary Equipment
(equipment shutdown, dampers,
door closures) operate properly
and are activated by the system
1. Verify valves in proper alignment.
1. Complete external inspection of
non-discharged cylinders to
ensure suitability for use.
2. Flexible Hoses
1. Pressure test hoses to ensure
suitability for use.
1. Protected Enclosure
1. Inspect the enclosure to verify
integrity and ability to maintain
As Part of
1. Visually Check:
a. Pipe hangers.
b. Heads for obstruction.
c. Piping for leaks.
d. Riser condition.
b. Panels secured and indicator
c. Notification appliances in place.
d. Manual stations in place and
e. Nozzles' covers in place.