1 January 2001
Table 2-19. Carbon Dioxide Systems ITM Tasks (Continued)
6. Auxiliary Equipment
closers, dampers) operate properly
and are activated by the control panel.
1. High Pressure Cylinders
1. Verify CO2 quantity by weighing
As Part of
1. Visually Check:
a. Check pipe hangers.
b. Check heads for obstruction.
c. Check piping for leaks.
d. Check riser condition.
b. Panels secured and indicator
c. Notification appliances in place.
d. Manual stations in place and
e. Nozzles' covers in place.