Emergency Electrical Power. Provide an emergency generator with
automatic starting and switching capability as described par. 2.5.7. Provide
emergency power to the following:
Loads as required by NFPA-101.
Electronic equipment in IFR and terminal equipment rooms.
Exterior security lighting and security systems.
400-Hz Power. Provide 400-Hz power in accordance with par. 2.5.9
when required by the BESEP.
Lighting. Design lighting in accordance with par. 2.5.6.
dimmer adjustable red lights in IFR control room.
Security. Air traffic control tower base buildings are normally
external security. If the facility is located within a restricted area of a
lower level of security, provide additional measures to meet the minimum
security requirements for the level of security assigned to the facility. The
level of security and the designer's responsibility for particular security
elements will be designated in the IDSEP. Refer to par. 2.6. Provide the
a) Electronic cipher door locks at interior entrance doors to IFR
and terminal equipment rooms.
b) Exterior doors in IFR and terminal equipment rooms with no
access hardware on the outside.
Additional Design Criteria.
Refer to Section 2 for facility design
requirements not addressed above.