Emergency Electrical Power. Provide an emergency generator with
automatic starting and switching capability as described in par. 2.5.7.
Provide emergency power to the following:
Loads as required by NFPA-101.
Exterior security lighting and security systems.
Uninterrupted Power Supply (UPS). Provide non-redundant UPS in
accordance with par. 2.5.8. Use the anticipated load to determine the size of
Security. Meteorological facilities are normally located within
security. If the facility is located within a restricted area of a lower
level of security or is located remote and outside of an established
restricted area, provide additional measures to meet the minimum security
requirements for the level of security assigned to the facility. The level of
security and the designer's responsibility for particular security elements
will be designated in the IDSEP. Refer to par. 2.6.
Additional Design Criteria.
Refer to Section 2 for facility design
requirements not addressed above.