c) RF shielding throughout the facility. Refer to MIL-HDBK-1195
and NAVFAC Instruction 11010.44. Shielding requirements shall be confirmed by
rectangular area bounded by Analysis, Intelligence Officer, ASWOC Support
Communications (ASCOMM), automatic data processing (ADP), and the UPS room.
Use stainless steel for 100 dB protection. Refer to DM-12.02, High Altitude
e) Built-in furnishings including counters, benches, service
windows, and storage racks.
f) Passage corridors a minimum of 5 feet, 6 inches wide and clear
g) Removable, modular, access flooring in the operations control,
mission control and evaluation, ADP and analysis rooms with 18 inches of
clearance provided between the floor panels and subfloor to accommodate wiring
and insulated piping. Refer to par. 184.108.40.206.
h) Hydraulic passenger elevator with removable protective padding
for transporting equipment (two-story facility only). Refer to NAVFAC DM-3.09
Elevators, Escalators, Dumbwaiters, Access Lifts, and Pneumatic Tube Systems,
and par. 220.127.116.11.
Facility and restroom areas readily accessible by the physically
Windows. Do not use windows unless specifically requested for
Mechanical Requirements. Design a thermostatically controlled
Ventilation. Provide ventilation for UPS and battery rooms in
accordance with par. 2.4. Provide ozone removal for analysis room by
ventilation to atmosphere.
Uninterrupted Power Supply (UPS). Provide non-redundant UPS in
accordance with par. 2.5.8. Use anticipated load to determine the size of the