Instructor's Station and Electrical Space. Each 19F
series trainer has its own instructor's station which, along
with the adjacent electrical space, houses most of the
electronic equipment associated with the device. Operations of
buildings associated with a given device are controlled from the
instructor's station. A single point ground plate is required
station and its accompanying electrical room under the raised
computer room flooring. The instructor's station and electrical
space should be waterproof from the outside weather.
Air Conditioned Space. The instructor's station and
adjacent electrical space should be designed as an air
conditioned office. When the instructor's station is adjacent
to a training compartment, it should be thermally insulated from
it, including structural members.
Temperature and Relative Humidity. Environmentally
control the instructor's station and the adjacent electrical
winter. Wintertime humidification and reheat for summertime
dehumidification is not a requirement. In accordance with
NAVFAC MIL-HDBK-1012/1, Electronics Facilities Engineering,
unit for an electronic equipment space. The instructor's
station and adjacent electrical room should be individually
controlled by independent thermostats.
Fire Protection. A fixed, fire protection system is
not required for the instructor's station or the adjacent
electrical space. However, portable CO2 extinguishers should be
provided by the facility contractor. Refer to par. 4.4 for the
requirements of portable CO2 extinguishers.
Window Glass. The window glass size and location
should be as indicated in the specific device sections. Glass
should be the insulated, shatter-resistant type. The bottom of
the window should be 900 mm above the floor.
Plugged Tap. Each instructor's station will have an
analog pressure indication for the firefighting water supplied