available for the transfer of large equipment. The door should
be used for installation and maintenance. A 1829 mm wide, 2134
mm high door should be located in the staging area to
accommodate large equipment on hand trucks. The door should
a) First floor burner room doors should be located at
each end of the burner rooms. They should be exterior doors
except for the northwest corner which should be in the extended
stair column. Second floor burner room doors should be accessed
from the stair columns as in the 19F1A.
b) A large hatch should be provided at the top of the
inclined stairs leading from the first floor and the second
126.96.36.199 Fireplaces. For exact dimensions of fireplaces
incrementally by compartment, see Table 9.
188.8.131.52 Instructor's Station. The instructor's station and
the electrical room below the instructor's station should be
similar to the rooms of the 19F1A and 19F1B. Interior
dimensions should be approximately 13 411 mm by 3048 mm.
Controls for the pit fire, B3, or B4 portion should be installed
in the instructor's station.
a) No hose drying area is required but provide the
following two items for hose drying: an outside hose drying
rack and a heated storage for rolled up 15 240 mm long hoses.
Rolled hoses should be stored vertically in storage racks.
Racks should be designed to hold two rolls high and be located
in the OBA locker.
b) P-250 training is a part of the 0412 course;
therefore, a facility is required. P-250 training is a
requirement for 19F3A and 19F3C structures.