Compressed Air. Low pressure compressed air shall be provided at
100 psi to all shop areas in accordance with NAVFAC DM-3. 5. Compressed air at
pressure and capacity as required shall be provided to weapons cleaning units
when the units are to be provided.
Plumbing. Plumbing shall be provided in accordance with NAVFAC
DM-3.1. Floor drains shall be provided in mechanical bays, electrical bays,
unpacking room, and supply room. Plumbing shall be provided for the battery
room as required in Section 5, Part 6 of this manual.
Noise and Vibration Control. All mechanical systems and equipment
shall be designed to limit noise and vibration in accordance with NAVFAC
ELECTRICAL REQUIREMENTS. Electrical systemw shall be provided in
accordance with NAVFAC DM-4.1, DM-4.2, DM-4.3, DM-4.4, and DM-4.6.
WEIGHT-HANDLING EQUIPMENT. Overhead bridge cranes or monorail hoists,
with capacity as required by the work done in the space, shall be provided for
the unpacking room of all weapons shops and for the mechanical bay of heavy
weapons shops. (See NAVFAC DM-38.1 for criteria for overhead bridge cranes or
SECURITY. Specific security requirements for the facility shall be
obtained from the security office of the activity. Design guidance for the
facility shall be obtained from NAVFAC DM-13.1, Physical Security.