should be power operated rolling steel doors. Pedestrian insulated doors may
be provided adjacent to the larger doors for convenience of entry if required
for the public works maintenance shop operation. Canopies or vestibules shall
be considered for the main entrance to the administrative area depending on
Movable Interior Partitions. Partitions subject to change in
floor plan layout shall be stock items with metal or gypsum board facings.
Floors. The ground floor of the facility shall be concrete
slab-on-grade. Resilient tile floor covering shall be used in offices. Exposed
concrete with hardener shall be used in shops, storage areas, and locker
Ceilings. Ceilings shall be exposed in all areas except the
administrative area and shop supervision offices or other special purpose
areas. Suspended acoustical tile ceiling shall be, provided in the
administrative areas. Inverted acoustical metal deck or other suitable
material for sound control shall be used for ceilings in the shop offices. A
concrete slab ceiling of the required tire rating shall be provided over the
flammable storage room in the shop stores.
Windows. Shop supervision offices and other similar interior
spaces shall have observation windows.
Equipment and Furnishings. Provide equipment and furnishings
as indicated in equipment schedules in NAVFAC P-272, Part One.
Material Handling Aisle. Mounted items shall not project
into the aisle more than 6 inches.
Areas with Special Requirements
Administrative Area. The administrative area shall comply
with requirements for the physically handicapped as stated in NAVFAC DM-1,
section 6, paragraph 10.
Carpenter Shop. Provide enclosure, including doors, taking
noise and dust control into consideration.
Moving, Rigging, and Wharf Building Shop. The roof structure
shall support a 2-ton capacity monorail hoist.
Shop Stores and Tool Room. Security ceilings at 10-foot
height or full height walls are required. The flammable storage area shall
have fire rated wall, door, and ceiling construction according to the nature
of the stored materials.
dust may accumulate. A finished ceiling shall be provided.
Paint Shop. The design of the paint shop shall comply with
requirements in NFPA 33.