ARCHITECTURAL AND ENGINEERING DESIGN REQUIREMENT
LEGEND and NOTES
One each OX, MCA, MV is required in both the headwall unit and the
Each overhead service column will contain 2 OX, 2 MV, 2 MCA, 1 NO and
1 NI. An additional MV will be provided on each wall as appropriate.
The medical gases specified will be per bassinet or infant station.
The medical gases specified will be per 6-8 bassinets or infant
stations. Where the LDR birthing room concept is used, a minimum of
one grouping will be provided in each LDR.
For equipment testing and calibration, equipment shall be tested with
the specific gas used in normal operation.
Provide valved regulator station for PA.
Each utility center requires 1 DCA and 1 DLV.
A natural gas outlet (counter mounted) and a lab air outlet (under
counter-mounted) will be provided at each dental work station as
shown in Appendix A.
contingency beds require 1 OX, 1 MV, 1 MCA per bed station. In
expansion situations in "peace time" facilities also provide 1
1 MV, 1 MCA per contingency bed expansion requirements noted in
program for design.
Facilities may use nitrogen for driving surgical handpiece in oral