request submission of 65 Percent Preliminary Working Drawings. The Design
Agent's Medical Facilities Design Office/Center, shall develop the
specific submittal requirements to define the S-5 level of design effort.
Comprehensive Fire Protection Design. All fire protection
provisions shall be summarized and submitted as a separate plan supported
by a fire protection design analysis, including fire protection drawings
developed during the Concept phase of the design. The fire protection
study shall include related design considerations and criteria that have
been coordinated among all the affected disciplines and shall serve as the
basis for the design, construction, and future operation of the building.
If required by the Design Agent, a completed Statement of Construction
will be provided at the completion of construction by the contractor.
Equipment Specifications. The AE shall develop specifications
for all equipment that does not have current guide specifications. Update
the specifications to permit procurement of the latest model of equipment.
Develop the specifications to accommodate at least three reputable
vendors of the same type equipment when practicable. Coordinate problem
items with the using Military Department. Include the scope of services
to be provided by mechanical and electrical contractors for installing
government furnished equipment. The Joint Schedule Numbers (JSN) or the
National Stock Numbers (NSN), within the MIL-STD 1691, shall not be used
as substitutes for contract specifications and detail drawings.
100 Percent/Final Submittal (S-6). The Design Agent's Medical
Facilities Design Office/Center, shall develop the specific submittal
requirements to define the S-6 level of design effort. When the design is
complete, the Design Agent will submit a copy of the final documents (i.e.
drawings, specification, cost estimate, instructions to bidders, etc.) to
DMFO. Along with this package, the Design Agent shall provide a
memorandum to DMFO certifying that the design has been completed and that
all technical requirements and cost criteria approved at the 35 Percent
Design stage have been incorporated into the Final Design.