16 APRIL 2004
Secondary service from the transformer shall connect to a main service over current
protection and disconnecting device.
Metering shall be provided. Either check metering on the Clubhouse, if primary
metering is in use, or secondary metering on the load side of the transformer, in
accordance with local utility or base requirements.
Voltage requirements may vary for overseas locations and should be verified before
Secondary service voltage shall be 208/120V, 3, 4 wire. (Therefore, interior
The MDP (main distribution panel) shall serve the large three phase mechanical
equipment and feed branch circuit panel boards. Provide separate panel boards for
the kitchen, general lighting and power, and single phase and smaller three phase
Run all circuits in steel conduits with insulated copper conductors.
Provide full size green insulating grounding conductor for each circuit.
All power wiring shall run concealed.
Recommended lighting levels are listed in Chapter 4 for the specific functional areas.
In general, provide lay-in fluorescent fixtures in offices and back-of-house spaces;
downlights and decorative, dimmable fixtures in the dining rooms; fluorescent strip
fixtures in mechanical and utility spaces; lensed fixtures in food preparation and
Provide manual toggle switches, dimmers and automatic lighting controls (occupancy
sensors, time clocks) for lighting as appropriate for the dining, kitchen, golf shop, back
of house and offices. Lighting controls shall meet the requirements of the local energy
Provide convenience receptacles, special configuration receptacles and power for
user's equipment and mechanical equipment.
6-3.6 Exterior Lighting Systems
Exterior lighting systems shall be designed to include the following provisions:
Provide pole mounted metal halide lighting for parking areas and low level metal
halide bollards for walkways.
Provide metal halide or compact fluorescent fixtures in exterior canopies and at
exterior door locations.
Provide pole-mounted metal halide for outdoor activities.
Provide time clock/photocell control for all exterior lighting.
6-3.7 Communication Systems
Considerations for providing appropriate communications systems support for the Golf
Page 61 of 65