6 December 2006
Including change 1, 7 December 2006
6-2.2.4 Before working near energized equipment at any substation, install suitable
barriers and warning signs.
6-2.2.5 Confirm that reactors and connected equipment are deenergized and
grounded before touching or approaching within the minimum working distances
6-2.2.6 Discharge surge arresters and stored energy devices in accordance with
manufacturer's recommendations or local instructions.
INSPECTIONS AND TRAINING.
Conduct inspections of lockout/tagout control procedures at least annually.
Train employees in the specific lockout/tagout control procedures with training
reminders as part of the annual control inspections.