26 September 2006
Warehouses (Piled or Rack Storage).
Water demands for warehouses containing rack storage or piled storage must
comply with paragraph 6-11.
Rubber Tire Storage.
Water demands for rubber tire storage must comply with paragraph 6-11.
Water demands for aircraft hangars must comply with paragraph 6-16.
Aircraft Acoustical Enclosures.
Water demands for these facilities must comply with paragraph 6-17.
Water demands for ordnance facilities must comply with paragraph 6-10.
Flammable and Combustible Liquid Storage.
Water demands for flammable and combustible liquid storage facilities must
conform to paragraph 6-12.
WATER DEMANDS FOR UNSPRINKLERED FACILITIES.
Water demands for buildings and facilities that are not fully sprinklered are based
on fire department hose stream requirements.
Hose Stream Demands for Unsprinklered Facilities.
Hose stream demands and duration requirements for facilities that are not fully
sprinklered are outlined in Appendix C. The following factors affect the water
demand and duration and must be considered to determine the specific demand
and duration within a given range in accordance with Appendix C:
Response time by fire department,
Type of construction,
Number of stories,
Building floor area, and