A 65 mm by (2) 40 mm wye gate.
d) Two 30 480 mm steel hose racks with strap,
NAVSHIPS Dwg. 805-860089.
Four 40 mm hose, 12 240 mm long Fed. Spec.
Two 1219 mm applicators.
Foam Station (FS). Foam hose station, supplied with
Refer to foam station diagram Appendix A, Figure A-21.
Single agent hose reel
b) A 40 mm hose, 38 100 mm long, MIL-H-24580, Hose
Assemblies, Synthetic Rubber, Noncollapsible, Firefighting
19F1A - 303 L
19F3-B1 - 303 L
19F3-B3, 19F3-B4, and 19F5 - 379 L
e) Electric foam proportioning pump (Blackmer pump
Model BXL - 1-1/4, Manufacturer Dwg. E-4638)
Controls as found on damage control deck
The 100 percent AFFF concentrate line should have a
valved bypass before it enters the concentrate tank arranged so
19 L AFFF cans can be filled at that location.
Foam Reel (FR). Foam reel station, supplied with
Refer to Appendix A, Figure A-21.
Single agent hose reel, Appendix A, Figure A-6.