Submarine Hose Station 2 (SHS2).
Hose station is
supplied with water and is floor mounted.
A 40 mm angle globe valve.
Refer to SHS1 above.
b) A 40 mm hose, 15 240 mm long, MIL-H-24606, Hose
Assemblies, Chlorosulfonated Polyethylene Impregnated, Double
Synthetic Jacket, With Couplings, Firefighting and Other Water
c) Floor mounted hose cabinet in accordance with
Appendix G, Figure G-9. The hose is rolled up and stored in the
Submarine Hose Station 3 (SHS3). Hose station is
supplied with water and is recessed into the wall. Hose station
should consist of the following as shown on NAVSEA Dwg.
608-4674414: (SHS3 is part of the combined submarine hose
A 40 mm hose, 15 240 mm long, MIL-H-24606
Fire hose rack per NAVSEA Dwg. 608-4674414
One applicator per BUSHIPS Dwg. 810-1385834
Two spanner wretches per NAVSHIPS Dwg. 810-4444647
Spanner wrenches and the applicator should be clamped
recessed area of the station. Clamps should be per
Dwg. 608-4674414. SHS3 should be recessed into a space
wall with dimensions of 1270 mm height from the floor to
the opening by 762 mm wide by 203 mm deep.
Combined Submarine Hose Station (CSHS). Hose station
is supplied with water and consists of SHS3 recessed into the
wall with SHS1 on a metal plate mounted to cover SHS3. The
metal plate should be removable and should be provided over SHS3
to hide SHS3. The plate should be designed to be removed by one
or two men. Clips or other methods of attachment should be
provided for attaching the plate over SHS3. SHS1 should be