permanently attached to the metal plate. A 40 mm angle globe
valve normally furnished with SHS1 should be provided next to
the combined hose station.
PKP Fire Extinguisher (PFE). A 12 kg portable PFE
should be provided with single AFFF foam reels, as shown on
appendixes floor plans, and should be in accordance with
Twin Agent Reels (TAR). The TAR and system have been
replaced by a single AFFF FR and a 12 kg portable PFE which
should provide a similar function to the TAR system.