26 September 2006
MORALE WELFARE AND RECREATION FACILITIES.
Clubs including officer, non-commissioned officer, and enlisted; bowling centers,
craft shops including hobby shops, woodworking, auto centers, and similar
facilities must be protected with automatic sprinkler systems.
Building two stories or greater, measured from the lowest grade, accessible to
people with severe mobility impairment must be protected with automatic
Building Four Stories or Greater.
Building four stories or greater, measured from the lowest grade, regardless of
occupancy must be protected with automatic sprinklers.
Facilities of Type III, Type IV and Type V construction three or more stories in
height must be protected with automatic sprinklers systems.
Any renovation of existing building of Type III, Type IV and Type V construction
over 465 m2 (5,000 ft2) must include automatic sprinkler protection.
MISSILE ALERT FACILITIES (MAF).
MAFs are the aboveground facilities that support underground ballistic missile
launch control centers.
Protect all missile alert facilities with a sprinkler system designed and installed in
accordance with National Fire Protection Association 13R, Standard for the
Installation of Sprinkler Systems in Residential Occupancies up to and Including
Four Stories in Height. Systems must be supplied from the existing domestic
water storage tank. Use dry-pendant or dry-sidewall heads or anti-freeze runs
for rooms/spaces exposed to freezing temperatures.
Thermal detection devices must be provided in rooms, areas and spaces that are
not protected by automatic sprinkler protection in accordance with NFPA 13R.