26 September 2006
Provide a dry fire hydrant installed on the domestic water tank to allow local fire
departments the ability to draft firefighting water during emergencies.
Facilities and equipment which are used for the receipt of alarm signals and
telephone calls for assistance, and dispatching of fire, police, or emergency
medical services personnel and equipment shall comply with NFPA 1221,
Installation Maintenance, and Use of Emergency Services Communications
HIGH RISE BUILDINGS.
High rise buildings must comply with NFPA 101 and:
The central control station must have exterior and interior access, a
1-hour fire rated barrier, and must be a minimum of 9 m (96 ft)
with a minimum dimension of 2.4 m (8 ft),
The central control station must also include air-handling system
status indicators and controls, a fire department control panel for
smoke control systems (includes visual status indicators and
controls), and schematic building plans indicating the typical floor
plan and detailing the building core, means of egress, fire
protection systems, fire-fighting equipment and fire department
Provide smoke proof enclosures.